|Place of Origin:||Guangzhou, China|
|Certification:||ISO9001, CE, SGS|
|Minimum Order Quantity:||>= 1sets|
|Packaging Details:||export standard wooden case(plywood), no need to fumigate, suitable for shipping.|
|Delivery Time:||1-7working days(depand on raw materials stocking)|
|Payment Terms:||L/C, D/A, D/P, T/T, Western Union, MoneyGram|
|Name:||1500L/H RO System Water Purification Plant||RO Membrane:||USA FILMTEC LCLE-4040 DOW (DuPont)|
|Application:||Pure / Industrial / Drinking Water||Pretreatment:||Sand/Carbon/Softener/PP|
|Electrical Power:||380V 50Hz 3Phase||Tank Material:||FRP/ Stainless Steel|
|Pipe Fitting:||SUS304/ U-PVC||Feed Water TDS:||<2000mg/L|
|Production Capacity:||1000 L/H||Desalination Rate:||>=97%|
1500L/H Water Purification Plant,
FRP RO Water Purification Plant
Stainless Steel 1500L/H RO System Water Purification Plant With Softener Filter For Drinking
What is a Water Softener?
A water softener is an appliance that is fitted to the mains water supply to a home or commercial premises to remove dissolved minerals (hardness salts). These minerals form lime-scale in pipes and boilers, when the water is heated, and soap-scum in bath water, laundry appliances and sanitary-ware. They are usually fitted close to the mains water entry point in a house but can be sited almost anywhere. Modern domestic softeners are so compact that they can be easily installed under the kitchen sink.
What does a Water Softener do?
Water softeners use a process called ion exchange. The softener unit contains a column filled with beads of a resin which remove the dissolved calcium and magnesium ions from the hard water flowing through it, replacing them with sodium. Periodically, (typically once a day) the softener regenerates the resin by washing with brine (sodium chloride solution), carrying the calcium and magnesium to drain, and leaving fresh sodium ions on the resin ready for the next treatment cycle. Regeneration is usually triggered automatically by either an electronic timer or mechanical water flow meter. The unit has to be refilled with salt (in the form of granules, small tablets or blocks) typically once a month.
1. Capacity: 1.5T/H Ion Exchange Resin Softener
Hardness of raw water:
Hardness of effluent water:
time or flow
Principle as photo
The hardness of the output water test by the "chrome black T reagent" showed blue is qualified (<0.03mmoL/L).