This is brackish water project, Myanmar is a landlocked country, lack of fresh water, clients local water is a little salty which can't used for daily life. Hence, they need we help to handle the local water and change into pure water^^
Production capacity: 6000liters per hour (6TPH)
Raw water quality: underground water TDS 3000-6000PPM
Pure water quality: used for produce animal feed TDS <200PPM
1. 6TPH RO system finished in our factory from Guangzhou China.
2. Arrange shipping to Myanmar
3. When goods arrived to clients address, our sale and engineer flight there to help installation^^
After raw water and electric all is ready, we start:
a. Fill the quartz sand and actived carbon into two big filter
2. Then connect all pipe fittings.
c. RO Membrane fill into the housing.
d. Finally do some testing, electric test in a stable voltage, sand and carbon do some baskwash,
RO membrane do some washing, then whole machine working well^^
e. Installation finished, and wait for whole day to check how its working.
f. Check the output water quality, before local water PH9.2, and now to to PH7.3.
g. Raw water TDS is 4011PPM, and output water conductivity is 62.2uS/cm (31.1PPM),
desalination acheived tp more than 99%. Best data for us^^
h. Many thanks for client hospitality and cooperation.
A wonderful 7days business trip on Mandalay!
Contact Person: Miss. Rose