Payment & Shipping Terms:
|RO Membrane:||USA DOW||Production Capacity:||20TPH (customized From 250L/H To 200T/H)|
|Recovery Rate:||50% - 75%||Electrical Power:||220V / 380V 3Phase Or Others|
|Membrane Housing:||FRP/ Stainless Steel||Control Valve:||Automatic/ Manual|
|Pipe Fitting:||SUS304/ U-PVC||RO Rack Size:||5000*900*1950MM|
|Application:||Drinking Water, Milk, Beverage, Leather, Electronic Production|
ion exchange water purifier,
ion exchange resin water filter
20000 LPH 20 Ton per hour RO purifying/purification drinking solar reverse osmosis water treatment
1). RO pure water equipment main parameters
RO pure water equipment
capacity of pure water : 20000l/h 25°C
general power: 128kw
electrical power: ac380v 35a 50hz
ro membranes: espa 8040
beforehand filter:4872 frp 2 items 3672 frp 1 item
out size of main machine (mm): 3500x1200x1920
out size of beforehand filter(mm):5000x1600x1920
2). Function of the machine:
|ro membranes auto wash and manual wash|
|ro membranes manual wash wite medicine|
|pure water high water level auto stop,low water level auto start|
|multi-phases pump protected without water|
|protected when no power ,poor power,larger electrical current|
|short circuit, creepage of electricity|
We use SUS 304 / FRP tank to fill quartz sand and active carbon.
The controlling machine is made of stainless steel, as well as .
All water water pipes is PVC material.
|1. RO system means reverse osmosis system, which is the most advanced technique in pure drinking water treatment.|
|2. This machine can be design for small or large scale water factory according to the output.|
|3. This machine follows four steps to purify raw water, make sure the most pure drinking water.|
|4. We design all kind of protecting measures against no power, poor power, larger electrical current, short circuit, creepage of electricity and so on.|
3). Design basis
1. Source of water:tap water, if not ,pls provide the report for water quality.
2. Water production specifications
Note: Water capacity will be changed when the water temperature is down 1 °C,
and water production would be decreased by 3%.
Desalination system: ≥97%
Water recovery: 50-75%
4). The system process
Raw water→ raw water tank→ raw water booster pump→mechanical filter→activated carbon filter (→water softener machine)→precise filter →(cleaning device) high-pressure pump→Reverse Osmosis Components→pure water tank(→Ozone device/UV device) →pure water.
Some parts function:
1.Raw water pump: provide needed pressure for every pre-treatment filter;
2.Quartz sand filter: use fiber glass as housing, fill quartz sand, it can filter big particles impurities, suspended substances, colloids etc. Important to remove iron and sediments you mentioned;^^
3.Activated carbon filter: use fiber glass as housing, fill activated carbon, remove color, odor, residual chlorine and organics substances;
4.Security filter: prevent large particles, bacteria, viruses into RO membrane, accuracy is 5µm;
5.High pressure pump: provide needed working pressure for RO system, ensure production capacity of pure water;
6.RO system: can remove particles, colloids, organic impurities, heavy metal ions, bacteria, virus, heat source etc. harmful substances and 99% dissolved salts.
7.Ozone generator(for bottled drinking): can continue to kill bacteria even water fill into bottled,viruses,cell damage,atc...
Please feel free to contact us. 8 professional sales waiting for your any new inquiry. Our term is reply to customers any mails within 12 hours!! ^^
Contact Person: Rose Chen