Payment & Shipping Terms:
|RO Membrane:||USA FILMTEC DOW||Production Capacity:||1TPH|
|Tank Material:||FRP/ Stainless Steel||Control Valve:||Automatic/ Manual|
|Pipe Fitting:||SUS304/ U-PVC||Application:||Drinking Water / Industrial Water|
|Pump:||CNP Stainless Steel||Certification:||CE / SGS/ ISO9001|
water softener machine,
softening water system
1TPH Water softener price , Automatic water softener system , industrial water softener
Water Softener Use a Process Called Ion Exchange. The Softener Unit Contains a Column Filled With Based Of a Resin Which Remove The Dissolved Calcium And Magnesium Ions From The Hard Water Flowing Through It, Replacing Them With Sodium. Periodically, (Typically Once a Day) The Softener Regenerates The Resin By Washing With Brine (Sodium Chloride Solution), Carrying The Calcium And Magnesium To Drain, And Leaving Fresh Sodium Ions On The Resin Ready For The Next Treatment Cycle. Regeneration Is Usually Triggered Automatically By Either An Electronic Timer Or Mechanical Water Flow Meter. The Unit Has To Be Refilled With Salt (In The From Of Granules, Small Tablets Or Blocks) Typically Once a Year.
The hardness of the output water test by the "chrome black T reagent" showed blue is qualified (<0.03mmoL/L).
1. Capacity: 1000L/H RO
2. Rated power: 2.5KW/H
|3. Rack Size: 1870*630*1850mm|
4. Voltage: 110V 415V , 50Hz / 60Hz, single phase/3phase
|2. Operating Temperature : 5°C - 39°C|
|6. Desalination rate : >=97%|
Industriral automatic water softeners, equipment used to reduce the hardness of water, in addition to remove calcium and magnesium ions in the softened water softening equipment in the process, does not reduce the total salt content of the water.
1.Automatic control valve for water softener.
2.Big inlet water contacting design for better water softener.
3.Easy installation and having a high flow rate.
4.Manal or Automatic control for flushing.
5.High pressure resistance; Innovative design; Refined structure.
6.Using ceramic moving valve disk, small rotation torque.
7.Abrasion resistance of sealing surface, outstanding and long-lived deal.
8.It could be operated with pressure directly.
4. Dual-Tank Water Softener
When a water softener is recharging, it is designed to disconnect from the water system, so it is basically out of commission. For this reason, the regeneration cycle is usually set to occur at night. If softened water is needed during the regeneration cycle, this can be problematic.
If the down time of the water softener is an issue, or if a family is large or lives where water is particularly hard, it may be smart to consider adual-tank water-softening unit with two resin tanks. With a dual-tank unit, when one tank is in use, the other is regenerating. As a result, softened water is being supplied continuously, without any break in service. And because these units operate on demand, they can be sized smaller than single-tank units.
Several models are available. One popular product, the Fleck 9000, has a fully adjustable valve that is controlled by a meter. When the water softener starts backwashing one tank, its control switches the water supply to the other tank, offering a continuous flow rate of 21 gallons per minute.
5. working principle
As water hardness mainly calcium and magnesium to form and that sodium ion exchange softening the principle of raw water through the sodium cation exchange resin , so that the water hardness components Ca2 +, Mg2 + and resin in Na + -phase switching, thereby adsorption of Ca2 +, Mg2 +, the water is softened . As representatives of the RNa sodium resin , the exchange process is as follows:
2RNa + Ca2 + = R2Ca + 2Na +
2RNa + Mg2 + = R2Mg + 2Na +
Contact Person: Rose Chen