Payment & Shipping Terms:
|RO Membrane:||USA FILMTEC DOW||Production Capacity:||1TPH|
|Tank Material:||FRP/ Stainless Steel||Control Valve:||Automatic/ Manual|
|Pipe Fitting:||SUS304/ U-PVC||Application:||Drinking Water / Industrial Water|
|Pump:||CNP Stainless Steel||Certification:||CE / SGS/ ISO9001|
water softener treatment systems,
softening water system
1TPH Water Softener System RO Water Treatment Equipment with Automatic 304 Tank
Water Softener Use a Process Called Ion Exchange. The Softener Unit Contains a Column Filled With Based Of a Resin Which Remove The Dissolved Calcium And Magnesium Ions From The Hard Water Flowing Through It, Replacing Them With Sodium. Periodically, (Typically Once a Day) The Softener Regenerates The Resin By Washing With Brine (Sodium Chloride Solution), Carrying The Calcium And Magnesium To Drain, And Leaving Fresh Sodium Ions On The Resin Ready For The Next Treatment Cycle. Regeneration Is Usually Triggered Automatically By Either An Electronic Timer Or Mechanical Water Flow Meter. The Unit Has To Be Refilled With Salt (In The From Of Granules, Small Tablets Or Blocks) Typically Once a Year.
The hardness of the output water test by the "chrome black T reagent" showed blue is qualified (<0.03mmoL/L).
1. Capacity: 1000L/H RO
2. Rated power: 2.5KW/H
|3. Rack Size: 1870*630*1850mm|
4. Voltage: 110V 415V , 50Hz / 60Hz, single phase/3phase
|2. Operating Temperature : 5°C - 39°C|
|6. Desalination rate : >=97%|
Industriral automatic water softeners, equipment used to reduce the hardness of water, in addition to remove calcium and magnesium ions in the softened water softening equipment in the process, does not reduce the total salt content of the water.
3. working principle
As water hardness mainly calcium and magnesium to form and that sodium ion exchange softening the principle of raw water through the sodium cation exchange resin , so that the water hardness components Ca2 +, Mg2 + and resin in Na + -phase switching, thereby adsorption of Ca2 +, Mg2 +, the water is softened . As representatives of the RNa sodium resin , the exchange process is as follows:
2RNa + Ca2 + = R2Ca + 2Na +
2RNa + Mg2 + = R2Mg + 2Na +
Contact Person: Rose Chen